The below information provides guidance on asbestos safety for trades and contractors involved in maintenance, repair or renovation work of concrete pool shells.
It covers how to:
- identify swimming pools/spas with Marblesheen (Marblelite) finishes that may contain asbestos
- prevent exposure to asbestos fibres during maintenance, repair or renovation work.
What is Marblesheen/Marblelite?
Marblesheen, also known as Marblelite, is a decorative coating applied to the surface of concrete pool shells with average thicknesses between 5-25 mm. It is primarily composed of white cement and white marble chips between 1-2 mm in diameter (see Figures 1 and 2 below).
If the Marblesheen coating was applied prior to 1990, it may include asbestos.
Identifying if a pool coating contains asbestos
The only way to confirm if a Marblesheen coating contains asbestos is to have a sample analysed by a National Association of Testing Authorities (NATA) accredited laboratory.
Prior to any maintenance, repair or renovation work occurring testing should be undertaken for:
- Marblesheen coated pools built before 1990 (all Marblesheen pools in this category should be assumed to contain asbestos)
- pools built before 1990 which have may been resurfaced (leaving the original Marblesheen coating in place underneath).
If testing has not occurred to pools built before 1990, it must be assumed they contain asbestos until they are tested.
If you are uncertain about what year the Marblesheen was installed, it is advisable to undertake testing prior to renovating or resurfacing.
Is there a risk of exposure to asbestos from Marblesheen coatings?
If the Marblesheen coating is in good condition and left undisturbed, it presents a low risk as it is non-friable and the asbestos fibres are bound to the cement.
However the effects of aging can result in deterioration of the surface, which in turn can create leaks. This deterioration may include:
- damage such as cracks, breaks and chips
- delamination of the coating from the concrete shell (creating drummy areas).
Deterioration may not be isolated to one area of the pool and depending on the circumstances, repairs may be extensive and require a complete resurfacing.
Complete resurfacing requires, at a minimum, removal of the old surface from around fittings and tiles to enable a flush finish for the new surface.
Complete removal of the Marblesheen is often necessary if the deterioration is extensive, or where any cracks or rust repairs to the pool shell require surface removal to complete the repair.
Maintenance, renovation or demolition of asbestos-containing Marblesheen
Any work involving the removal or disturbance of Marblesheen coatings assumed or confirmed to contain asbestos must be done in accordance with the Work Health and Safety Regulation 2011 (WHS Regulation).
The table below outlines regulatory and licensing requirements for asbestos removal and asbestos-related work.
|Minor repair work and/or removal of 10 m2 or less of asbestos containing material (ACM)
||No asbestos removal licence required, however must undertake asbestos-related and/or asbestos removal work in accordance with the WHS Regulation 2011.
|Removal of more than 10 m2 of ACM
||Must be undertaken by a licensed asbestos removalist (class A or B licence) and all removal work must be in accordance with the WHS Regulation 2011.
Further guidance on managing risks associated with asbestos and asbestos containing material can be found in the:
Removal or repair of Marblesheen coating generally requires the use of power tools to break away the Marblesheen. The use of power tools will generate airborne asbestos fibres and other dusts including silica. Queensland laws prohibit the use of certain tools and work methods when working with ACM.
When working with or removing asbestos-containing materials:
Transport and disposal of asbestos-containing Marblesheen
All debris must be double bagged or double wrapped in 200 µm plastic and disposed of at an approved waste disposal facility. Weight limits may apply for transporting asbestos waste.
Find out more about transport and disposal of asbestos waste.